Control of electric underfloor heating and thermal servos in combination with a room temperature controller top unit.
Adaptive zero-point switch-off
Connecting auxiliary units is possible.
The load is switched off automatically. Delay times can be set to one of five levels, cannot be re-triggered.
Test run for function testing.
Operation with neutral conductor connection.
Combination with KNX RF operating top unit, 1-gang/2-gang
Switching actuator channel, 1-gang or heating actuator, 1-gang
Sensor channel, 1-gang or 2-gang.
Local control of System 3000 insert possible.
Wireless control of other KNX devices as sensor possible.
Insert function selection for switching: NO/NC operation, staircase function, scene function, blocking function, time delays. Auxiliary input can be used as an additional operating point for the System 3000 insert or for wireless control of other KNX devices as a sensor.
Insert function selection for room temperature controller: Control of 230 V servos, heating mode, cooling mode, heating and cooling mode, PWM and 2-point controller, absolute and relative setpoint setting, heating requirement control incl. cascading, valve protection function.
AC 230 V, 50/60 Hz
0.1 to 0.5 W
Ohmic switching current:
16 A (AC1)
Connected load at 35 °C
HV LED lamps:
typically 400 W
Compact fluorescent lamp:
typ. 500 W
HV halogen lamps:
Gira tronic transformers:
Fluorescent lamps, uncompensated:
Switching current for motors:
920 VA (115 µF)
without, 1 min, 5 min, 30 min, 60 min
in device box pursuant to DIN 49073
-25 °C to +45 °C
If the ambient temperature is higher than 35 °C, the connected load must be reduced.
Additional figures available in the media database
The optimum interaction of various Gira products for homes can now be experienced and compared "live". With the Gira Design Configurator, which is available on the Internet or as an app, diverse frame variants from the Gira switch ranges can be combined with selected functions in various colours and materials